With the MWEBplus system, it is possible to constantly monitor single-battery safety luminaires from a central location. The emergency luminaires report their current status via LAN network to a PC with a web browser, which takes over the evaluation and control of the entire system. 125 self-contained emergency luminaires can be installed according to the general circuit diagram indicated below. Using signal amplifiers, the MWEBplus can be extended to create a MultiDigitplus system for monitoring up to 7875 luminaires. Up to 63 signal amplifiers can be used. The bus line does not need to comply with any particular requirements; its structure can be T-shaped, star-shaped, linear or even mixed. Bus line polarity needs not to be considered.
The address of the signal amplifier for the safety luminaires is stored in a microcontroller and must therefore be provided when the system is ordered. Operation in connection with briefing of operating staff by an RZB employee is available at a cost.
If you have any technical queries or you require support for your planning, please contact your sales office.
Monitoring system for RZB self-contained luminaires with .04 coding